FIND A SALES REPRESENTATIVE
To find your local product representative in the United States, enter your zip code and press the Search button.
The LXVN55Q garage luminaire with optional integral sensor is available with an optical distribution designed to replace HID lighting systems up to 175w MH or HPS. Typical parking garage applications include retail centers, industrial parks, schools and universities, public transit and airports, office buildings and medical facilities. Mounting heights of 8 to 14 feet can be used based on light level and uniformity requirements.
LXVN55Q Benefits & Features
Low Profile Die Cast Aluminum Housing, ½" Coin Plugs with O-rings for Conduit or External Sensor. Built-in Sensor Housing with Color-Matched Polycarbonate Cover. A Clear Cover will be Provided When a Sensor is Ordered.
Listing & Ratings
CSA: Listed for Wet Locations, ANSI/UL 1598, 8750.
(Damp Locations When Used with VNQM.); IP66 Sealed LED Compartment.
Textured Architectural Bronze or White Powdercoat Finish Over a Chromate Conversion Coating. Custom Colors Available Upon Request.
Molded UV-Resistant Acrylic Optical Lens Designed for Garage Lighting Applications.
Included Easy-Hang Bracket Fits Standard 4" Electrical Box, Allowing One-Person Installation. Optional Quick-Mount/Pendant Bracket Available.
30w Array: 28; System: 30.5; (Up to 100w HID Equivalent)
37w Array: 37; System: 41; (Up to 100w HID Equivalent)
48w Array: 48.7; System: 53.9; (Up to 175w HID Equivalent)
Electronic Driver, 120-277V, 50/60Hz or 347V, 50/60Hz; Less Than 20% THD and PF>0.90. Standard Internal Surge Protection 6kV. 0-10V Dimming Standard for a Dimming Range of 100% to 10%; Dimming Source Current is 150 Microamps.
Fixtures Ordered with Factory-Installed Photocell or Motion Sensor Controls are Internally Wired for Switching and/or 1-10V Dimming Within the Housing. Remote Direct Wired Interface of 1-10V Dimming is Not Implied and May Not Be Available, Please Consult Factory. Fixtures are Tested with LEPG Controls and May Not Function Properly With Controls Supplied By Others. Fixtures are NOT Designed for Use with Line Voltage Dimmers.